The DuraVent DVL 8" diameter 90 degree elbow is used to offset the stove pipe for horizontal (through the wall) installations.
90 degree elbows should be installed a minimum of 12" above the stove collar to maintain a proper draft.
If you have a rear vent wood stove use a Tee instead of a 90 degree elbow when connecting to the back of the stove.
DuraVent DVL will connect directly to the AllFuel HST Stove Pipe Adapter for a seamless transition to AllFuel HST Class-A chimney pipe and components.
Note: DuraVent DVL double wall black stove pipe is intended for interior use only. This means that it is meant to connect your appliance to your Class-A chimney system. It should not be installed through combustible materials like walls or ceilings or be exposed to outside weather conditions.
- Inner Diameter is 8"
- Outer Diameter is 9"
- Listed to ULC S641
- Vertical run has 6" clearance to walls/combustibles
- Horizontal run has 8" clearance to ceilings
- .016" stainless steel inner wall with .018" galvanized outer wall
- Subtract 3/4" for installed length
- Outer wall painted black